Marianne Schaefer in Bricks & Bucks on June 5, 2019
This is not a Hollywood thriller about seven days in May. This is the astounding true story of a recent ten-day drama at a 47-unit co-op in Prospect Heights, Brooklyn, sparked by a gas leak which, if not successfully addressed, would have changed the life of every shareholder in the co-op.
“Behind all our efforts was the fear that the gas could be shut down for several months,” says Thomas Sussewell, chief operating officer of the co-op’s management company, Goldin Management. “That’s what usually happens, especially since this is a pre-war building from 1924.”
Day 1: On Thursday, May 16, National Grid installs a new state-of-the-art gas meter in the co-op. During installation, the gas is shut off.
Day 2: On Friday, May 17, an inspector from National Grid performs the mandatory pressure test on gas lines before restoring service. “We failed the pressure test,” says super Felipe Rodriguez. “There was a one-inch elbow going to the domestic line where they found a leak. The gas remained shut down and our residents had no hot water. [National Grid] told us we need a special certified plumber to fix the problem.”
Goldin Management’s go-to master plumbers didn’t have the special license for such jobs that has been required since January. “To get a plumber and have them work on it very quickly was an exercise,” says Sussewell. “They had to jump us in front of the line.” ABR Plumbing & Heating shows up at 3 P.M. and fixes the leaking elbow.
Day 3: On Saturday, May 18, National Grid is unable to perform another pressure test because neighborhood streets are closed for a marathon on Eastern Parkway.
Day 4: On Sunday, May 19, nobody is working – and residents are furious. “There are all these personal dramas playing out,” says Sussewell. “The board was very helpful dealing with the shareholders’ frustrations, which freed us up to deal with the gas lines.”
Day 5: On Monday, May 20, the pipes fail the pressure test again. “It turned out that on 85 feet of pipes, all elbows connecting these pipes have to be changed,” says property manager Albert Guglielmo. “When you connect old pipes to new pipes, it’s like a chain reaction, it’s spreading like cancer. Now it’s a monster.” The plumbers work frantically into the night.
Day 6: On Tuesday, May 21, the tension escalates. “We changed three-inch pipes and three-and-a-half-inch couplings,” says Rodriguez, the super. “That means now the Department of Buildings will have to do their own inspections to make sure the pipes can hold the pressure.”
Day 7: On Wednesday, May 22, the DOB promises to show up in about two weeks. Guglielmo says “No, no, no!” and starts calling DOB supervisors – without success.
Day 8: On Thursday, May 23, co-op board president Alan Mass recommends getting city council majority leader Arna Lipkind involved. “And what do you know?” says Guglielmo. “The inspector from the DOB says he will come the very next day.”
Day 9: Friday, May 24, the building passes the DOB test in the afternoon. National Grid still has to come back for another pressure test after the DOB has confirmed that all is clear. The DOB inspector has his laptop with him, and he loads the result into the DOB main computer system. At 8 P.M. the plumber calls Guglielmo to tell him the inspection result is not on the DOB database.
Day 10: Saturday, May 25, the plumber informs Guglielmo that the DOB test result is now showing up in the system. National Grid claims there are no inspectors in the field on the Memorial Day weekend. Anticipating this problem, Guglielmo has the mobile phone number of an inspector, and he knows he’s working that day nearby in Queens. After numerous phone calls from Guglielmo, the inspector shows up at the co-op in the afternoon. “The test took more than three hours,” says Rodriguez. “They do the pressure test, the nitrogen test, they make sure all the air is out of the line, that the boiler turns on, that the regulators and everything is working. Then they filled out some forms and turned on the gas.”
Ten tense days had come to an end – at a cost of about $22,000.
PRINCIPAL PLAYERS – Property manager: Goldin Management. Plumbing contractor: ABR Plumbing & Heating.
Engage, enrage, ask questions and give answers with your community of board members. Submit your questions and comments here!
Co-op and condo board business broken down into bite-sized bits - 2 stories each week. Read now on all digital devices.